An important advantage of a TB-
Many natural gas compressors must be installed outdoors with lengthy piping required
to bring high pressure gas service to the point where it is used. A G-
The system has 2 gas inlets, one if your building supply pressure is less than 1
psi and a second if utility natural gas pressure between 1-
On the high pressure outlet many G-
Find out more about how G-
Limited Pressure Booster customization is available for supply gas pressure, output
pressure and flow volume. Contact G-
There is no expensive administrative time to secure permits, no special safety or environmental site requirements. Maintenance is simple to perform and parts are not expensive. Training required for operation and maintenance is minimal.
Simple indoor installation without special site preparation
Avoid complex installation permitting issues with a G-
CE Compliant for use in
European Union countries
CSA International is accredited in the United States by the Occupational Safety and Health Administration (OSHA) as a Nationally Recognized Testing Laboratory (NRTL), and in Canada by the Standards Council of Canada (SCC).
Whatever your pressure and flow requirement there is a G-
There are separate gas inlets for supply of natural gas at <1 psi or between 1-
Install your Torch Booster “anywhere” -
Single cabinet includes both Booster and Cooler functions and measures 50 1/2” wide, 33” deep and 32” tall.
Weight is 550 lb. Power requirement is 208V single phase 60 hz 30 amp iin North America/230V single phase 50 hz 30 amp worldwide.
Supply gas should be ¼ psi to 5 psi in a minimum 1 1/2” diameter pipe.
Electric service is 208V single phase 30 amp 60 Hz in North America or 230V single phase 30 amp 50 Hz worldwide. Low pressure supply pipe must be at least 1 1/2” diameter.
These Torch Boosters use a set of flexible hoses that connect the Booster to the Cooler. A pump in the Cooler Module cycles oil between the Booster and the Cooler to remove excess heat from the Booster. Electrical power is slaved from the Torch Booster so the Cooler Module starts when the Torch Booster starts. The Booster cabinets measure 28” wide, 24” deep and 20” tall. The Cooler Module is 20” wide, 18” deep and 16” tall, weighs 107 pounds and can be stacked on top of the Torch Booster to minimize footprint space. Electric service is 208V single phase 30 amp 60 Hz in North America or 230V single phase 30 amp 50 Hz worldwide. Low pressure supply pipe must be at least 1 1/2” diameter.
When you need natural gas at pressures between 60 -